Key Changes In The 18th Edition
The 18th Edition of the IET Wiring Regulations is here!
The 18th Edition of the IET Wiring Regulations has become mandatory for electrical installation from 1st January 2019. It has some new regulations for the industry from the changes. These focus on energy efficiency and provide further safety measures for installers to provide for their customers.
There are lots of changes in the 18th Edition. These include new and revised regulations, new chapters and restructured sections.
So with the big blue book now available where do you look to discover these changes? Here, are the key changes that you need to know:
The scope has been extended to include an extra category (section 730 catering for electrical shore connections & inland navigation vessels). Section 730 contains the particular requirements for this added special location.
Chapter 46 is new and Chapter 53 has been rewritten. Part 6 is restructured & the regulations for inspection & testing move to new chapters and get new regulation numbers.
There are several new definitions and a few existing definitions that have been amended. For example, “Departure” is a new definition.
Departure is explained as an intentional decision to not fully comply with BS7671. This must be accompanied by a declaration from the designer that the safety levels achieved are not less than full compliance with BS7671 would provide.
A new appendix on energy efficiency is included within the 18th edition. Appendix 17 makes recommendations for the design construction & assembly of the installation for optimising efficiencies in the use of electricity.
Only Use Approved Parts
Devices & components used in low voltage assemblies e.g. Consumer Units, Distribution Boards etc. shall only be those that have been declared suitable for that purpose by the manufacturer of the assembly.
If in doubt ask the manufacturer of the assembly to confirm compatibilities.
Note; if a deviation from manufacturer instructions is introduced then the person introducing the deviation becomes the manufacturer.
Arc Fault Detection Devices
AFDDs have been included in Chapter 42. These devices provide additional protection against fires that are caused by arc faults in AC final circuits.
Arc fault detection devices (when used) should be installed at the origin of each final circuit that is are being protected, AFDDS should be installed in consumer units and/ or distribution boards.
In the schedule of inspections, under the section dealing with consumer units & distribution boards, there is a reference to check for the AFDD six monthly test notice, similar to the requirements for RCDs & RCBOs.
Also in the schedule of test results form there is a new tick box for AFDDs which allows the installer to record operation of the manual test button on the AFDDs, again this is similar to RCDs & RCBOs.
Within the 17th Edition of the Wiring Regulations, the requirements of surge protection were determined through risk assessment methods. Now, overvoltage protection is required in certain circumstances.
For example, where there is risk of serious injury or of loss of life, where many co-located people are affected, where there is an interruption to public services or commercial/industrial activity. Other requirements are contained in 443.4.
For circumstances where overvoltage protection is not required, a risk assessment can be carried out. If a risk assessment is not carried out, overvoltage protection must be provided.
Want To Know More?
If you’d like some more information Electrium have put together some of the key changes for you to see. Get some insights from clicking the boxes below:
Contact Electrical Wholesale is an electrical wholesaler based in Birmingham, West Midlands and Cannock, Staffordshire. If you have any questions on the new wiring regulations don’t hesitate to get in touch with us.